OPENING PROTECTIVES for > 3 stories Exit Stair (NFPA 101 Table 184.108.40.206).
(Applicable to all occupancy type except one and two family dwelling)
||WALLS AND PARTITIONS
||FIRE DOOR ASSEMBLIES
||DOOR VISION PANEL MAXIMUM SIZE
||FIRE WINDOW ASSEMBLIES
|Staircase and Vertical Shafts||1-hr||1-hr||Maximum size tested||W-60|
The Exit Separation shall have not less than a 1-hour fire resistance rating where the exit connects three stories or less, NFPA 101 – 220.127.116.11.1 (1)
- Refer also to complete listing of Opening Protectives.
- Code Reference used is NFPA-101 2012 edition unless otherwise noted.
- These information is not complete and intended to be used as quick references only, always refer to NFPA or your local codes for complete information.